MSHA Alert: Electrical Safety
The Mine Safety and Health Administration (MSHA) has released the investigation report on a November 18, 2013, fatality at a crushed stone mine. The incident involved a 33-year-old contract electrician foreman with 14 years of experience who was injured when he contacted energized conductors after pulling cable for a new pump that was being installed while working on a 480-volt electrical enclosure. He died four days later in a hospital.
MSHA recommends the following best practices for working with electricity:
Ensure that persons are trained on all electrical tests and safety equipment necessary to safely test and ground the circuit where work is to be performed.
Positively identify the circuit on which work is to be conducted.
De-energize power and ensure that the circuit is visibly open for circuits being worked on and circuits near the work area.
Lock and Tag! Place YOUR lock and tag on the disconnecting device.
Use properly rated Personal Protective Equipment (PPE) including Arc Flash Protection such as a hood, gloves, shirt, and pants.
Ensure ALL electrical components in the enclosure are de-energized by testing for voltage using properly rated test equipment.
Install warning labels on the terminal covers of bottom feed circuit breakers warning that “Bottom terminal lugs remain energized when the circuit breaker is open.”
To view the full accident report, click here.
MORE FROM Aggbeat Online
SUBSCRIBE & FOLLOW
- Mike Rowe talks about the dirty topic of educating future workers428 Views
- McLanahan Rolls Out Four Key Products226 Views
- Rod Martin receives AggMan of the Year 2013 Award198 Views
- MSHA Assistant Secretary of Labor Main updates NSSGA on recent agency actions194 Views
- NSSGA debuts its new strategic plan172 Views